Payment & Shipping Terms:
|Product Name:||4 OPzS200||Application:||Telecom Wind|
|Size Of Battery:||103*206*354mm||Terminal:||M8|
|Weight:||12.8 KG||Case:||ABS, SAN|
2V 4 OPzS200 Tube Vented ABS Opzs Batteries Solar Energy Storage Application
Designed life for floating charge is 20 years according to IEC60896-11;
Rubber separator with floating electrolyte technology;
High strength ABS material for cover and SAN material transparent container;
Wide temperature scope of application (-15~45℃);
Best temperature of application (20±5℃);
Special filter installation for acid fog proof;
Transparent container, convenient to observe;
Super long service life.
|Nominal Voltage||2V||Nominal Capacity (C10)||200Ah (1.80V @ 20℃)|
|Dimension||Length 103mm||Approx. Weight||Without electrolyte:12.5kg /with electrolyte:17.2kg|
|Width 206mm||Max Charging Current||40A|
|Height 354mm||Internal Resistance||Full charged@20℃: 0.0008 Ohm|
|Total Height 409mm||Self Discharge||3% of capacity declined per month@20℃|
|Capacity Affected by Temp. (10HR)||40℃||20℃||0℃||-15℃|
Alarm & Security system
Alternative Energy System
High Power Backup Supply
The battery should be kept clean and dry. Wring tight the acid-proof bolt, and
The installation site should be kept clean and dry. With the best temperature
about 20 C, the battery room should be given ventilation once weekly.
No dust falls in the battery.
Clean the acid-bolt every month with pure water to remove the filth.
The battery pack has high voltage, so direct contact or indirect contact through
wet objects with any conducting cable may result in vital injury. The battery pack
is energy-storing equipment, so never short-circuit the battery pack during
operation and maintenance in any way.
Do not wear watch, hand chain, bracelet, ring and other conductive objects
Only qualified and professional personnel are allowed to install, operate and
maintain the equipment.
Heat kills batteries. Avoid installation and/or operation in close proximity to heat
sources of any kind. While the operating temperature range is -15°C to 45°C,
and ideal service life will be realized when the battery is operated in an ambient
temperature of 20°C (for cyclic service applications, a range of 5°C to 35°C is
If the battery is to be installed in an air or water tight container, ventilation must
be provided. Batteries may generate ignitable gases which must not be
contained. Because of this, batteries should not be installed near spark
Avoid installing the battery in an atmosphere where organic solvents or
adhesives may be present. Do not clean the battery with oils, thinners or similar
substances. Use water only. The case and cover of the battery is ABS plastic
resin which may suffer damage from these chemicals.
Contact Person: Song Gao