Payment & Shipping Terms:
|Product Name:||CB6360||Application:||Security, Emergency|
|Size Of Battery:||161*87*163mm||Terminal:||FO-21 / FP-01|
36AH 6V SLA Battery , Agm Lead Acid Battery For Emergency Alarm Application
Sealed and maintenance free operation.
Non-Spillable construction design.
ABS containers and covers(UL94HB, UL94V-0) optional.
Safety valve installation for explosion proof.
High quality and high reliability.
Exceptional deep discharge recovery performance.
Low self discharge characteristic.
Flexibility design for multiple install positions
Designed life for floating charge is 3~5 years (20℃)
AGM valve regulated sealing technology
High strength ABS material for container & lid
Wide temperature scope of application (-15~45℃)
Best temperature of application (20±5℃)
No leaking, safe and reliable
Standing or lying down for using, convenient to transport and install
High sealed reaction efficiency, little loss of water, no need to add distilled
water or electrolyte, simple to use and maintain
Low self-discharge rate.
|Nominal Voltage||6V||Capacity||C10||36Ah (5.25V, at 25℃)|
|Nominal Capacity (C10)||36Ah (5.25V,at 25℃)||C5||28.8Ah (5.25V, at 25℃)|
|Dimension||Length 161mm||C3||27Ah (5.25V, at 25℃)|
|Width 87mm||C1||19.8Ah (5.1V, at 25℃)|
|Height 163mm||Internal Resistance||Approx. 8 mΩ (25℃)|
|Total Height 169mm||Max Short-duration Discharge Current||720A(25℃)|
|Weight||Approx. 6.20kg||Terminal||FO-21 / FP-01|
Standby power of electric power company, Telecom Company, Bank, Stock
System and Security Company
Standby power of all kinds of emergency illumination and system
Uninterruptible Power Supply(UPS)
Standby power of guard against theft and alarm system
Power source for Power-assist vehicle, electromotive tool and toys
Standby power of solar energy system
The unique construction and sealing techniques of the battery guarantee leak
proof operation in any position with no adverse effect to capacity or service life.
Electrolyte Suspension System
All batteries utilize an electrolyte suspension system consisting of a high
porosity, glass fiber material which in conjunction with plates, totally absorb and
contain the electrolyte.
CGB batteries incorporate a built-in design that controls gas generation and
induces recombination of more than 99% of gases generated during float or
Maintenance Free Operation
There is no need to check specific gravity of the electrolyte or add water to
batteries during float service life. In fact, there is no provision for this type of
Low Pressure Valve Regulated System..
All batteries are equipped with safety release valves, designed to operate
between 1.5 and 6 psi (10-40kPa) and automatically reseal. Hence, there is
never an excessive accumulation of gas within the battery.
Heavy Duty Grids
Heavy duty lead calcium tin alloy grids provide an extra margin of performance
and service life in either float or cyclic applications.
Cyclic Service Life
More that 600 discharge/recharge cycles can be realized from CGB CB and HR
batteries, dependent on the average depth of discharge.
Float Service Life
CB, HR and SE Series batteries have an expected life span of 3 to 5 years in
float service applications.
Self Discharge - Shelf Life
The self discharge rate at room temperature is approximately 3% of rated
capacity per month.
CGB Batteries may be operated over a broad range of ambient temperatures.
Deep Discharge Recovery
The batteries recover their capacities even after repeated deep discharges.
Ensure that our operations and products meet or exceed government
Monitor, control and eliminate, where possible, all environmental emissions,
discharges and waste generated by our operations.
Develop products that will have a minimum effect on our environment.
Alarm & Security system
Emergency Power Systerm
Fire-safety Emergency System
Banks & Financial Centre
Hospital& Testing Laboratories
Don’t charge in the sealed container.
Please use cotton cloth to clean, if the battery is broken down and leak
electrolyte. Please wash your skin when touch the electrolyte.
You should be careful and regular check when use the battery. To avoid the
battery don’t work. You should change the battery if the capacity is not full or has
been damage, especially after one year using.
Don’t put the battery in the fire, or it will explode.