Payment & Shipping Terms:
|Product Name:||8OPzV800||Application:||Medical Equipments|
|Size Of Battery:||191*210*646mm||Terminal:||M8|
800 Ampere Hours Sealed Lead Acid Opzv Battery For Medical Equipments 8OPzV800
|Nominal Capacity (C20)||800Ah (1.80V @ 20℃)|
|Weight||Approx. 60 kg|
|Internal Resistance||Full charged@20℃: 0.0004 Ohm|
|Max Charging Current||160A|
●Design life is above 18 years in float application and cycle life is above 1400
times in 80% DOD (Depth of Discharge) term;
● New porous PVC－SiO2 separator with low-internal resistance;
● High strength ABS material for container & lid;
● Wide temperature scope of application (-15~45℃);
● Best temperature of application (20±5℃);
● No leaking, safe and reliable;
● Standing or lying down for using, convenient to transport and install;
● High sealed reaction efficiency, little loss of water, no need to add distilled water or electrolyte, simple to use and maintain;
●Tubular positive grids to avoid active material from shedding..
● Cable Television
● Electric Utility
● Alarm & Security system
● Control Equipment
● Medical Equipment
● Railroad Utility
● Photovoltaic System
● Alternative Energy System
● High Power Backup Supply
● New porous PVC－SiO2 separator with low-internal resistance
● Initial capacity is above 95%, the remaining capacity is above 90% when
storage for 3 months (20 ºC)
● Remarkable high rate discharge performance
● Gel electrolyte with high conductance rate
● In order to assure service life, the batteries should be correctly inspected and maintained. The maintenance methods of GEL batteries are recommended as follows:
● Monthly Maintenance
Implement the under-mentioned inspection every month:
Keep the battery-room clean.
Measure and record the ambient temperature of the battery-room.
Check each battery’s cleanness; check damage and overheating trace of the
terminal, container and lid.
Measure and record the total voltage and floating current of the battery
● Quarterly Maintenance
Repeat monthly inspection.
Measure and record floating voltage of every on-line battery. If more than two
cells’ voltage is less than 2.18V after temperature adjustment, the batteries
need to be equalization charged. If the problem is still existing after adopting
above-mentioned measures, the batteries need yearly maintenance or even
three years’ maintenance. If all methods are ineffective, please contact us.
● Yearly Maintenance
Repeat quarterly maintenance and inspection.
Check whether connectors are loose or not every year.
Make a discharge test to check with exact load every year, discharging
30-40% of rated capacity.
● Three-year Maintenance
Operation manual for OPzV series
Make a capacity test every year after three years’ operation. If the capacity of
the battery decreases to lower than 80% of rated capacity, the battery should
Operation and Maintenance
● Insufficient Charge
If the floating voltage is not set correctly (too low or not amend according to
temperature), the battery system will in an insufficient charge state for a long
period of time. When the electricity is out, the battery may not be able to work
because the acid is saltilized and the capacity is decreased.
● Over Charge
Please do not neglect the performance of rectify to transfer floating charge to
equalization charge. If the rectify cannot transfer charge modes because of its
wrong performance or no adjustment, the battery system is always in an
equalization charge state. Thus may cause serious problems for battery, such as
water loss, life decrease, heat out of control, deformation, etc.
● Too low or too high temperature
We have mentioned that too low temperature will affect the capacity of battery.
While too high temperature will also cause problems, such as water loss, life
decrease, heat out of control, deformation, etc.
● Too low end voltage
The end voltage is also an important parameter for battery. The battery shall
stop discharging when reach a certain voltage (The normal end voltage is
1.8Vwith 10-hour rate). If the end voltage is too low, it will be difficult to
recharge the battery and decrease the charge efficiency, thus reduce the life of
●Ensure that there is a correct connection between the battery a nd the charger; do
not reverse the terminal connection.
●Do not use any type of organic solvent to clean the battery.
●Do not charge the battery at the temperature over 50 ºC.
Contact Person: Song Gao